We’ve had a major failure in our redundant CRAC (Computer Room AC) that handles cooling for our Santa Rosa Data Center a Colocation Facilities. The redundant systems have taken over and we believe that the situation is under control. Our vendors are en route, more information forthcoming.
Update: 14:15:14 PDT. The redundant system is functioning properly and the room temperature has nearly stabilized. We believe the failure was caused by a refrigerant leak due to the failure of a pressure release safety valve. The faulty valve has been isolated and technicians are en route with refrigerant to recharge the system.
Update: 17:45:30 PDT. The failed system has been recharged (with over 800 lbs of refrigerant) and restored to service and appears to be functioning correctly.