This Friday, starting at 9AM, one of the three UPSes that serves our Santa Rosa datacenter will be undergoing its annual preventative maintenance. The maintenance is fully scripted with our vendor and no interruption of services are expected. During the maintenance window our standby genset will be kept running should our PG&E service fail. -Kelsey and Russ
Update: Fri Feb 18 19:49:15 PST 2011, the schedule maintenance has been completed with some complication. One of of the bypass contactors jammed preventing the UPS from going back online. While the contactor eventually actuated and the UPS was brought online, it’s replacement will be scheduled as soon as possible. -Kelsey and Russ.